last cell purchased june 2009 (30K g inground cement pool) is faltering just like the last one, same story, inaccurate faulty LOW salt readings when actual salt levels are fine, resulting in no chlorine production when reading is below 2500ppm. I am done with goldline, aquarite, completely unreliable product, built to die and suck your money on replacement cells. So I am trying to manipulate the system to have it generating chlorine until I decide to purchase a new one from a DIFFERENT manufacturer.
I put resistor on the temp wires as done by the engineer and set temp to 88F and can get an instant salinity reading well into the 3000's, then I lock that reading by switching to superchlorinate and back to auto.
Only problem is this locking of the salt reading is temporary, and the instant readings the system does eventually brings the number down and I have to start process again. Is the engineer still around? anyone like him on here that knows if we can do something with these insant readings that bring down the main salt reading (as it is taking an average of the readings).